Low Voltage Surge Protective Device Type 2 4P Uc 385V Poles For Power Supply
|Place of Origin:||Dongguan China|
|Certification:||CE / SGS / ISO9001|
Payment & Shipping Terms:
|Minimum Order Quantity:||200 piece|
|Packaging Details:||export package / Negotiate|
|Delivery Time:||5-15 days after payment|
|Payment Terms:||T/T, L/C, Western Union|
|Supply Ability:||60000 pieces per month|
|CertificationCE,CQC:||CE / CQC / SGS|
Uc 385V low voltage surge arrester,
4P surge protective device type 2,
Uc 385V surge protective device type 2
AC 40kA 1P 2P 3P 4P(+NPE) Type 2 Surge Protection for Power supplies
The surge arrestors OBV5-C40-LT meet the type 2 requirement class according to IEC 61643-11. These devices protect low-voltage consumer systems from overvoltages of all types and are available in single-pole to four-pole versions. The use of high-performance varistors permits a rapid response time and a low protection level, without any line follow current. If circumstances are uncertain and there is a risk of fire from an overload, the internal cut-off unit disconnects the arrestor from the mains if necessary. In addition, the QR code printed on the arrestor allows disary. In addition, the QR code printed on the arrestor allows direct access to the online installation instructions.
* High arresting capacity
* Visual status display
* Available with optional remote signalling
* Simple standard hat rail mounting
* Labelled connections
* Voltage encoding
|Maximum continuous voltage AC||Uc||V||275/320/385/440|
|SPD to EN 61643-11||Type 2|
|SPD to IEC 61643-1||class II|
|Nominal discharge current (8/20< s)||In||kA||20|
|Maximum discharge current (8/20< s)||Imax||kA||40|
|Voltage protection level||Up||kV||< 1,3/1,5/1,8/2,0|
|Response time||tA||ns||< 25|
|Maximum back-up fuse||A||125|
|Protection rating||IP 20|
|Max. cable cross-section flexible (fine-wire)||mm²||25|
|Max. cable cross-section rigid (single wire/multi-wire)||mm²||35|
1,Protect electric system and on-loading electrical apparatus from thunder and instantaneous over-voltage.
2,Protect transmission of Ethernet signals with 48V DC / 34V AC power supply circuits against
lightning induced surges.
3,Enhanced surge protection.
4,For mounting on 35mm DIN rails acc. to EN 60715.
5,It can effectively ensure the equipments work properly.
·Easy installation or retrofit.
·Fail-safe /self-protected designRemote indicator (optional) with 3pin NO/NC contact.
·IP20 finger-safe designVisual indicator.
●Motor controls systems
●Power transfer equipment
● AC drives
Necessity of lightning protection detection:
1.lightning protection detection surge protector can resist lightning disasters and ensure life safety.
The damage of lightning to buildings can only be avoided through lightning protection devices. Lightning directly hits buildings or equipment exposed to the air, and various overhead metal cables will cause equipment damage, and even more serious fires will cause people to bring damage to the equipment. Unnecessary property damage. Professional lightning protection testing companies can do professional lightning protection. The lightning protection testing is to check whether the installed lightning protection devices or structural equipment are reasonable, whether the protection conditions meet the requirements, and whether the electrical safety meets the standards. If it fails to meet the requirements, the lightning protection inspection company will promptly put forward corresponding rectification opinions;
2.Lightning protection device test results meet national standards.
The detection results of lightning protection devices of well-known domestic lightning protection inspection companies are based on the standards of the national professional departments, and the lightning protection inspection companies also use the relevant lightning protection technical standards and standards of the country and various departments as the measurement index. Professional lightning protection testing companies also have relatively more testing content. A series of lightning protection testing software and equipment involved in the detection process can objectively make standard judgments on lightning protection work, so the accuracy of the data results is also higher;
How to choose a suitable power arrester:
When choosing lightning arresters to protect different types of equipment in an area, the following factors should be considered comprehensively:
●The intensity of thunderstorms in the area, the number of days of thunderstorms and the parameters of the maximum discharge current and the probability of occurrence;
●The value of the protected equipment;
●The level of impact resistance of the protected equipment;
●The social importance of protected equipment;
●Determine the power surge arrester with different protection voltage UP and discharge current;
Technology SPD parameter(Note:According to user requirement ,can be customized Uc=140V,440V,550V,voltage range of range of the SPD):
|Type No.||Rated Voltage(V) Un||Continuous Voltage Uc(V~)||Standard Discharge Current In(KA)|
Max Discharge Current
|Protection Level(KA~)||Response Time(ns)|
Q: Can I get some samples?
A: Yes, Sample orders welcomed.
Q: Can I use my own Logo or design on goods?
A: Yes, Customized logo and design on mass production are available.
Q:What is the delivery time?
A: 3 days for samples, 7-15 days for mass production.
Q: What is the payment term?
A: T/T, L/C at sight, West union , Paypal, etc.